Wow, never seen that before, although we don't have many of the C units. Has the membrane housing split and the bolts sheared off? how was the membrane affected?
I've had a push fit connector on the reject line shear off the end plate, but nothing like that.
Thanks for that.
Repaired RO using existing membrane, output flow was very low.
flushed with RO clean 2 and RO clean 5, output flow shot up to 2.6L/ min
adjusted flow back down to 1.2L/min and all is good.
Checked disinfection log, patient had not disinfected/descaled RO ever.
We had a patient who didn't disinfect or descale for about 2 years.
Very hard water and no softener for the first year, then never changed the salt on their softener.
This is with a centurion which don't like hard water at all.
Never had a single problem with the RO - weird !!